How to operate the Poolclub household heat pump with floor heating
Nowadays, many households use floor heating or radiator heating. Central heating is mainly compared in terms of energy, mainly in coal and electricity; in terms of energy, household heating is compared primarily to gas and electricity. After years of research and technical precipitation, air energy heat pumps have been gradually applied to the heating market of "coal-to-electricity" shock.
How to operate the Poolclub air source heat pump with floor heating?
There is a process of heating up the floor heating. After installing floor heating in a new or old house, the heating time will be longer when it is used for the first time every year. After the air source heat pump is turned on, the temperature of the heating should not be set too high, and it needs to rise slowly, giving the indoor furniture, walls, wallpaper, etc. enough time to adapt to avoid cracking and mildew in the table, walls, and wallpaper.
If the temperature of the indoor floor heating is set too high at the beginning or even set to the indoor temperature that the heating cannot reach, it is not conducive to the evaporation of indoor water vapor, and the indoor heat will consume more energy due to the large temperature difference, and the Poolclub heat pump host will be under high load for a long time Operation will affect the service life of the heat pump host. Even if the heating water temperature is set high and the heating time is shortened, the indoor temperature will take a certain amount of time to rise to the set temperature. If the temperature of the indoor heating is gradually increased, the comfort, energy saving and safety of indoor heating are all available.
How to adjust the indoor thermostat of the air source heat pump?
The Poolclub air source heat pump needs to control the temperature of the water supply, thereby regulating the temperature in the room. If the water supply temperature of 50°C is used, the indoor temperature is set to 20°C, and the indoor temperature can be reached quickly; if the water supply temperature of 35°C is used, the indoor temperature is also set to 20°C, and the indoor temperature will take longer to reach. Therefore, the temperature of the water supply determines the time for the indoor temperature to reach. In general, when the temperature of the water supply is below 45°C, the energy efficiency of the air source heat pump host is relatively high, and it is more energy-efficient to use, and the indoor temperature can quickly reach the set temperature. Of course, the premise is that indoor Underfloor heating is designed and laid to standard. If the thermal insulation of the house is very good, when the water supply temperature is set at 35°C, the indoor set temperature can also be reached, and the energy saving is even higher.